Check out the below photos of an installation we completed at a fast food outlet in Hertford as part of an 'Experience Of The Future' refurbishment.
2 York units were installed for the kitchen and lobby with a 50% increase in cooling capacity compared to the existing old units.
The kitchen extract fan was also upgraded from 1.8m3/sec to 2.8 m3/sec and controlled by an ABB Inverter.
York-Johnson Controls - 2 x ARG40 gas fired heating and R410a cooling packaged units.(Brochure attached for more information).
RHF BW500 Kitchen Extract fan with 'ABB' ACH550 inverter.
For more information, please get in touch with us at email@example.com